Main range of productModicon X80 product or component typeAnalog output module electrical connection1 connector 20 ways Isolation between channelsNon isolated Complementary measurement error<= 0.25 % of full scale 0...60 °C0.1 % of full scale 25 °C temperature drift45 ppm/°C 0...20 mA45 ppm/°C 4...20 mA common mode between channels>= 80 dB isolation voltage1400 V DC between channels and ground1400 V DC between channels and bus detection typeOpen circuit 4...20 mAShort circuit 0...20 mA load impedance ohmic<= 350 Ohm 0...20 mA<= 350 Ohm 4...20 mA output levelHigh level analogue output number8 analogue output typeCurrent 0...20 mACurrent 4...20 mA analogue output resolution15 bits + sign supplyInternal power supply via rack conversion time<= 4 ms maximum conversion value0...21 mA 0...20 mA0...21 mA 4...20 mA fallback modeConfigurablePredefined status LED1 LED green RUN1 LED per channel green channel diagnostic1 LED red ERR1 LED red I/O product weight0.15 kg current consumption150 mA at 3.3 V DC74 mA at 24 V DC Environment vibration resistance3 gn shock resistance30 gn ambient air temperature for storage-40...85 °C ambient air temperature for operation0...60 °C relative humidity5...95 % 55 °C without condensation IP degree of protectionIP20 directives2012/19/EU - WEEE directive2014/30/EU - electromagnetic compatibility2014/35/EU - low voltage directive product certificationsCECSAULRCMMerchant NavyEAC standardsEN 61000-6-2EN 61000-6-4EN 61131-2EN 61010-2-201 protective treatmentTC operating altitude0...2000 m2000...5000 m (with derating factor) Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsUser guideSizeAdd to My DocumentsModicon X80 - Racks and Power Supplies, Hardware Reference Manual (Version 02)Modicon M580 - RIO Modules, Installation and Configuration Guide (Version 08)Modicon M580 Standalone System Planning Guide for Frequently Used Architectures (Version 08)BrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsMarine certificateSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.
Dimensions DrawingsModules Mounted on RacksDimensions(1)With removable terminal block (cage, screw or spring).(2)With FCN connector.(3)On AM1 ED rail: 35 mm wide, 15 mm deep. Only possible with BMXXBP0400/0400H/0600/0600H/0800/0800H rack.
a in mm
a in in.
BMXXBP0400 and BMXXBP0400H
BMXXBP0600 and BMXXBP0600H
BMXXBP0800 and BMXXBP0800H
BMXXBP1200 and BMXXBP1200H
Connections and SchemaWiring DiagramIx+ pole input for channel x.COMx- pole input for channel x, COMx are connected together internally.
The current loop is self-powered by the output and does not request any external supply.