Main range of productEasypact CVS100...250 product or component typeCircuit breaker device short nameCVS100B device applicationMotor poles description3P protected poles description3d Earth leakage protection (Vigi add on)Without [In] rated current100 A ( 65 °C ) breaking capacity codeB network typeAC [Icu] Breaking capacity40 kA Icu conforming to IEC 60947-2 at 220/240 V AC 50/60 Hz20 kA Icu conforming to IEC 60947-2 at 440 V AC 50/60 Hz25 kA Icu conforming to IEC 60947-2 at 380/415 V AC 50/60 Hz utilisation categoryCategory A trip unit nameMA trip unit technologyMagnetic trip unit rating12.5 A ( 65 °C ) protection typeShort-circuit protection (magnetic) Complementary network frequency50/60 Hz control typeToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront [Uimp] rated impulse withstand voltage8 kV conforming to EN/IEC 60947-2 [Ics] rated service breaking capacity15 kA conforming to IEC 60947-2 440 V AC 50/60 Hz25 kA conforming to IEC 60947-2 380/415 V AC 50/60 Hz40 kA conforming to IEC 60947-2 220/240 V AC 50/60 Hz mechanical durability30000 cycles electrical durability12000 cycles conforming to IEC 60947-2 415 V In connection pitch35 mm contact position indicatorYes short-time pick-up adjustment type IsdAdjustable [Isd] short-time pick-up adjustment range6...14 x In instantaneous pick-up adjustment type IiAdjustable instantaneous pick-up adjustment range6...14 x In height161 mm width105 mm depth86 mm Environment electrical shock protection classClass II standardsEN 60947-2IEC 60947-2 product certificationsGOSTIEC ambient air temperature for operation-25...70 °C ambient air temperature for storage-50...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.